Our editors will review what you’ve submitted and determine whether to revise the article.Join Britannica's Publishing Partner Program and our community of experts to gain a global audience for your work! SHARE Facebook Twitter
- The history of construction
- Roman achievements
- The first industrial age
- The second industrial age
- Development of building service and support systems
- Modern building practices
- Low-rise residential buildings
- Low-rise commercial, institutional, and industrial buildings
- High-rise buildings
The enclosure systems for high-rise buildings are usually curtain walls similar to those of low-rise buildings. The higher wind pressures and the effects of vortex shedding, however, require thicker glazing and more attention to sealants. The larger extent of enclosed surfaces also requires consideration of thermal movements, and wind- and seismic-induced movements must be accommodated. Window washing in large buildings with fixed glass is another concern, and curtain walls must provide fixed vertical tracks or other attachments for window-washing platforms. Interior finishes in high-rise buildings closely resemble those used in low-rise structures.
Life-safety systems are similar to those in low-rise buildings, with stairways serving as vertical emergency exits; in case of fire all elevators are automatically shut down to prevent the possibility of people becoming trapped in them. Emergency generator systems are provided to permit the operation of one elevator at a time to rescue people trapped in them by a power failure. Generators also serve other vital building functions such as emergency lighting and fire pumps. Fire-suppression systems often include sprinklers, but, if none are required by building codes, a separate piping system is provided with electric pumps to maintain pressure and to bring water to fire-hose cabinets throughout the building. There are also exterior connections at street level for portable fire-truck pumps. The fire hoses are so placed that every room is accessible; the hoses are intended primarily for professional fire fighters but may also be used by the building occupants.
Vertical transportation systems are of vital importance in high-rise buildings. Escalators are used on lower floors for moving high volumes of people over short distances. A few retail or educational buildings have escalators for up to 10 stories. The principal means of vertical transport in tall buildings is the roped elevator. It moves by a direct current electric motor, which raises and lowers the cab in a shaft with wire ropes running over a series of sheaves at the motor and the cab itself; the ropes terminate in a sliding counterweight that moves up and down the same shaft as the cab, reducing the energy required to move the elevator. Each elevator cab is also engaged by a set of vertical guide tracks and has a flexible electric cable connected to it to power lighting and doors and to transmit control signals. Passenger elevators range in capacity from 910 to 2,275 kilograms (2,000 to 5,000 pounds) and run at speeds from 90 to 510 metres per minute; freight elevators hold up to 4,500 kilograms (10,000 pounds). The speed of elevators is apparently limited to the current value of 510 metres per minute by the acceleration passengers can accept and the rate of change of air pressure with height, which at this speed begins to cause eardrum discomfort.
Elevator movements are often controlled by a computer that responds to signals from call buttons on each floor and from floor-request buttons in each cab. The number of elevators in a building is determined by the peak number of people to be moved in a five-minute period, usually in the early morning; for example, in an office building this is often set at 13 percent of occupancy. The average waiting time for an elevator between pressing the call button and arrival must be less than 30 seconds in an office building and less than 60 seconds in an apartment building. The elevators are usually arranged in groups or banks ranging from one to 10 elevators serving a zone of floors, with no more than five elevators in a row to permit quick access by passengers. In a few very tall buildings the sky lobby system is used to save elevator-shaft space. The building is divided vertically into subbuildings, each with its own sky lobby floor. From the ground floor large express elevators carry passengers to the sky lobby floors, where they transfer to local elevator banks that take them to the individual floors within the subbuildings.
Plumbing systems in tall buildings are similar to those of low-rise buildings, but the domestic water-supply systems require electric pumps and tanks to maintain pressure. If the building is very tall, it may require the system to be divided into zones, each with its own pump and tank.
The atmosphere systems in high-rise office buildings are similar to those of low-rise, with conditioned air distributed by a ductwork tree using the VAV system and return air removed through ceiling plenums. The placement of air-handling equipment can be done in two ways. One uses centralized fans placed about every 20 floors, with air moved vertically through trunk ducts to and from each floor; the other uses floor-by-floor fan rooms to provide air separately for each floor. There is usually a central refrigeration plant for the entire building connected with cooling towers on the roof to liberate heat. The central refrigeration machines produce chilled water, which is circulated by electric pumps in a piping system to the air-handling fans in order to cool incoming air as required. Incoming air is heated in winter either by piping coils through which hot water is circulated by pumps and piping from a central boiler, or by electric resistance coils in the air-handling units. In residential high-rise buildings cooling is typically provided by window air-conditioning units, and heating by hot-water or electric resistance radiant systems. There is limited use of centralized cooling, in which chilled water from a central refrigeration plant is circulated to fan-coil units near the building perimeter; a small electric fan within the unit circulates the air of the room over the chilled water coil to absorb heat.
Electrical systems for high-rise buildings are also very similar to low-rise types. The major difference is that, if the building is exceptionally tall, the utility company may bring its high-voltage lines inside the building to a number of step-down transformers located in mechanical equipment spaces. From each step-down transformer the distribution of electricity is similar to that of a smaller building.